Tipton – Wolverhampton – Mastervolt XS fault code HW FAIL 3
Mastervolt XS was reported with a fault code HW FAIL 3.
Attended site and carried out preliminary inspection.
The inverter was found to have been located in an unsuitable location within an enclosure in full sun.
Mastervolt inverter mounted on south facing external wall in cabinet
This probably contributed to its early failure due to the build up of excessive heat in a poorly ventilated enclosure.
The inverter was found to be beyond economical repair.
The inverter was replaced with a SMA Sunny Boy SB2.5-1VL-40 complete with on board wifi monitoring and relocated to a cooler...
Court House Green - Coventry – Fronius IG TL ERROR state 447
System reported as intermittent fault.
After an initial inspection an insulation resistance fault was located on the array DC wiring.
A second visit would be required to remove panels and investigate further.
Severe damage was found to DC cables on roof which was repaired with the array reinstated.
Fronius IG TL error state 447
Fronius IG TL error state 447
Poor workmanship also contributed to the insulation resistance fault due...
Bingham – Nottingham – Samil Power Solar River 4000TL-D
Samil Power Solar River 4000TL-D
Samil Power Solar River 4000TL-D inverter reported to have failed, no yield from system.
System thoroughly checked and tested, no fault could be found.
Inverter re-started and was found to be working ok.
System left in working...
Over January we have looked back on some of the solar PV system and inverter maintenance work we have been doing, so the following blogs are a few of the inverter maintenance and maintenance or installation cases we have dealt with since the Summer which we thought you may find interesting........
- Blackfordby – Swadlincote - SMA Sunny Boy SB1500
- Radcliffe on Trent - Nottingham – Fronius IGTL
- Radcliffe on Trent – Nottingham – SMA Sunny Boy SB2500HF-30
- Hamilton – Leicester – Power One PVI-3.6-OUTD error E031
- Court House Green - Coventry – Fronius IG TL error state 447
- Tipton – Wolverhampton – Mastervolt XS fault code HW FAIL 3
- Hinckley – Growatt 3000MTL - service visit
- Walsall – Mastervolt XS4300 showing INSULATION fault
- Long Eaton – Nottingham – Schuco/Sunny Boy...
As a Fronius Service Partner this enquiry originated from the Fronius help desk. We were informed that the Fronius inverter had fault code 417 showing which indicates a DC card failure.
The customer was offered a replacement DC card with a 1 year warranty or a replacement Fronius Galvo 1.5 inverter with a full 5 years’ manufacturers warranty. In this case the customer decided it would be prudent to opt for the latest technology and have a new solar inverter.
As part of the works the customer requested that the solar inverter be relocated. It was also noted as part of our site visit that the DC isolator switch was none lockable, a regulatory requirement. This was also rectified as part of the inverter replacement/relocation work.
Fronius solar inverter replacement and repair
We are delighted to announce C Gascoigne Ltd are now SolarEdge Certified Installers offering SolarEdge inverter installation and maintenance services.
If you are to experience any problems with your Solar Edge inverter or inverters, optimizers or power boxes, get in touch with our team of solar PV
As SolarEdge certified installers we can install, replace, fix or repair, speaking to SolarEdge on your behalf ; checking if your system is under warranty and coordinating the repair process as easily as possible for you. We can do this on all SolarEdge systems in place of your original installer.
Contact us via telephone on 01509 341971 or via e-mail email@example.com or visit our contact page here
You can be confident we...